Wire & Cables
Wire & Cable
Quad 600V URD
QUADRUPLEX 600V SECONDARY URD | SPEC P7328D-AG
|INSULATION:||Cross-Linked Polyethylene XLP|
Used for secondary distribution and underground service at 600 volts or less, either direct burial or in ducts, in areas with soft soils where rodents are not present.
Secondary power distribution up to 600V in areas with soft soils where rodents are not present.
Conductors are stranded, compressed 1350-H16/H26 aluminum insulated with vulcanized interlinked polyethylene. Neutrals are triple yellow extruded stripe. Neutrals have sequential footage markers. Conductors are durably surface printed for identification. Three phase conductors and one neutral conductor are cabled together to produce the quadruplex cabled together to produce the quadruplex cable configuration.
Paige’s quadruplex or paralleled 600 volt secondary UD cable meets or exceeds the following applicable ASTM specifications.
- B-231 Aluminum 1350 Conductors. Concentric-Lay-Stranded
- B-609 Aluminum 1350 Round Wire. Annealed and Intermediate Tempers, for Electrical Purposes.
- B-786 19 Wire Combination Unilay-Stranded Aluminum Conductors for Subsequent Insulation.
Paige’s quadruplex 600 volt secondary UD cable meets or exceeds all applicable requirements of ICEA S-105-692 for crosslinked polyethylene insulated conductors and UL Standard 854 for Type USE-2.